How to adjust the fuel supply of diesel generators? @ QingdaoGenerator Rental18810769755
The average supply of diesel generator sets directly affects the use of diesel generator sets. Do you know how to adjust the fuel supply of diesel generators?
Prepare two glass measuring cylinders. If you cannot find a graduated cylinder today, you can also replace it with two identical vials.
(2) Remove the high-pressure oil pipe joint connected to the injector with the cylinder with too much (or too small) fuel supply.
(3) Remove the high-pressure pipe joint, and the high-pressure pipe joint is connected with the injector through the cylinder for normal oil supply.
(4) Insert the two tube ends into two measuring cylinders (or vials) respectively.
Use the starting installation of the generator to rotate the fuel pump oil.
When there is a certain amount of diesel in the equivalent cylinder (or vial), comparing the amount of oil on the level gauge can determine whether the amount of oil supplied is too large or too small. If replaced by a small bottle, it can be weighed and compared. It can adjust the relative position of the fork or the ring gear on the fuel conditioning lever (ie, the gear lever) of the injection pump. The P-type pump can be conditioned by rotating the flange sleeve.
Qingdao Generator Rental Center
When using the analog method to adjust the fuel supply, the operation must be meticulous.
Article from: Welcome to Qingdao Generator Rental Center! http://cwfdc.com
You may be interested: the harm of poor quality diesel to diesel generators